Fiberglass Reinforced Faced (Proprietary Core) (Simulated Panel Type or Flush) Swinging Door for installation in up to 20 minute locations (with or without hose stream-see table below). For use in any "Category C - Standard" frames. These doors may also be installed in frames listed in "Category C - Proprietary" in accordance with the frame manufacturer's individual listing. A fire rated compression weather strip is required.
Cylindrical/Mortise/Deadbolt/Latches with maximum 2-3/4" backset/Card Reader/Surface Mounted Vertical Rod Fire Exit Devices/Rim-Type Fire Exit Devices/Viewers/Protection Plates/Surface Mounted Closers/Surface or Kerf Mounted Door Bottom/ Arch Top and Round Top Door Configurations.
Maximum Size of Openings
Single Swing (with hose stream) 3'0" wide x 6'8" high
Standard and Double Egress Pairs - Not Allowed
UL-10C (Positive Pressure) (2009)
NFPA 252 (2008)
CAN4 S104 (1985)
All assemblies are identified by a label or marking bearing the wording, "Listed (Product)", a time interval, temperature rise (if applicable), a serial number and the WHI Certification Mark.
(Unless otherwise specified, all Fire Doors have a nominal thickness of 1-3/4".)
CSI Code 08 10 00 Doors and Frames
CSI Code 08 15 00 Plastic Doors
Fire Resistance 20 Min w/Hose Stream PP Cat A Door
Swing Single Swing
Listed or Inspected LISTED
Report Number 100354358MID-001
Criteria CAN4 S104 (1985)
Criteria NFPA 252 (2008)
Criteria UL 10(c) (2009)
Intertek Services Certification
Listing Section CATEGORY A - DOORS - NO ADDITIONAL
EDGESEALING SYSTEM REQUIRED